## How close does a vent need to be to a drain?

For a 1 ½-inc pipe the vent should be 42 inches away at the most while a 2-inch pipe must have a maximum distance of 5 feet. For pipes that have a diameter of 3 inches the distance is 6 feet and for a 4-inch pipe the most it should be away from the vent is 10 feet.

## How far does the vent have to be from the trap?

Distance of fixture trap from vent.

Size of Fixture Drain, Inches Distance Trap to Vent
1-1/4 2 ft 6 in
1-1/2 3 ft 6 in
2 5 feet
3 6 feet

## How far can a toilet be from a vent stack?

6 feet

According to the UPC, the distance between your trap and the vent should be no more than 6 feet. In other words, for the vent to work properly, it needs to feed into the drain line within 6 feet of the trapways that connect to it.

## Where should a vent pipe be placed?

Vent pipes must be installed so they stay dry. This means that they should emerge from the top of the drainpipe, either straight vertically or at no less than a 45-degree angle from horizontal, so that water cannot back up into them.

## Can a toilet shower and sink share a vent?

Wet venting is most common in conjunction with toilets and sinks; the drain for the sink is also the vent for the toilet. It can also be used for a variety of other applications but due to the following rules this is the most convenient and common situation to run into.

## Can you put an elbow in a vent pipe?

Note: You may have vent piping, but you still cannot use the tight 90-degree elbow — sometimes called a “vent elbow” — if the joint is below the water level, which is usually at the level of the sink.

## Can a toilet vent run horizontal?

There is no problem with running your vent pipes horizontally as long as you remember that there should be a minimum clearance of 6 inches above the spill line. What is a spill line? This is the level where the water starts to overflow from the rim of the sink, toilet, or tub.

## Can you use one vent for the whole bathroom?

In new construction, the simplest way to vent a bathroom group is usually to install a single vertical vent pipe behind the bathroom sink. This works as long as all the plumbing fixtures connect to the main drain line in the floor within 6 to 10 lineal feet of the sink drain.

## How high above the roof should a vent pipe be?

Unless a roof is to be used for any purpose other than weather protection, extensions of vent pipes through a roof should be terminated at least 12 inches above the roof. The vent should be extended at least seven feet above the roof if it is to be used for something other than weather protection.

## Does a plumbing vent have to be vertical?

Plumbing vents need to be straight on the vertical. This is necessary to avoid any vapor locks from occurring. When there is a bend in the vent pipe, moisture accumulates and is trapped.

## How far should sewer vent pipe stick out of a roof?

The International Plumbing Code (IPC), requires plumbing vent pipes to extend vertically at least 152 mm (6 in.) above a roof, per Section 905.5, “Vent Connections and Grades.” Additionally, vent pipes must be at least 305 mm (12 in.) away from a vertical surface.

## Does a vent pipe have to go through the roof?

It does not have to go through the roof. From the plumbing code (I have the 2003 edition), P3103: It must not be less than 4 feet directly beneath a door, openable window or other air intake of the building or adjacent building.

## Can plumbing vents terminate horizontally?

Not more than one-third of the total permitted length, in accordance with Table 703.2, of a minimum-sized vent shall be installed in a horizontal position. Exception: Where a minimum-sized vent is increased one pipe size for its entire length, the maximum length limitation shall not apply.

## Does a vent pipe need to be sloped?

All vent and branch vent pipes shall be so graded and connected as to drain back to the drainage pipe by gravity. Vent and branch vent pipes shall be free from drops and sags and be sloped and connected as to drain by gravity to the drainage system.