CSST Bonding is used to reduce the possibility and severity of arcing between conductive systems when energized by a lightning strike on a CSST gas pipe or nearby. The CSST must be permanently bonded to the grounding electrode system of the electrical service of the home in which the CSST is installed.
How do you bond CSST?
Quote from the video:
Quote from Youtube video: Metal. Then run the minimum six gauge copper wire through the bonding clamp. This wire is then attached to the homes grounding network via the grounding bus bar in the panel.
What is direct bonding of CSST?
A direct bond consists of a listed grounding clamp and separate conductor run from the gas piping to the grounding electrode system. The 2018 NFGC requires a direct bond for Corrugated Stainless Steel Tubing (CSST) gas piping that does not have a listed arc resistant jacket or coating.
Does CounterStrike Csst need to be grounded?
Unlike TracPipe®, there are no additional bonding requirements for CounterStrike® imposed by the manufacturer’s installation instructions. CounterStrike is to be bonded in accordance with the National Electrical Code NFPA 70 Article 250.104 in the same manner as the minimum requirements for rigid metal piping.
Can you bond CSST to ground rod?
That means that the bonding conductor for CSST can be connected to the metallic water piping coming into the home, a ground rod at the exterior, or anywhere else on the service grounding electrode system.
How do you bond a gas line to an electrical panel?
Quote from the video:
Quote from Youtube video: So the non-current carrying conductive part of this metal furnace is likely to become energized. So what do you have to do well i says well then you're going to have to bond it in accord.
Does flex gas line need to be grounded?
FAC does not require bonding. This is because they are connected to a bonded (if properly installed) gas-distribution system. It is between 1–6 feet long. FAC are commonly found between the home’s gas-supply lines and the gas equipment OR appliance.
Should gas piping be grounded?
CSST Gas Lines Must Be Grounded
Since 2009, US building codes have required CSST to be bonded and grounded for safety, but that was not required during the first 18 years. If you have CSST in your home and gas supply line work was done there since 1990, you need to be sure it is safe.
Does black CSST need to be grounded?
The IFGC and IRC recognize advances made by CSST manufacturers to produce a more robust, arc-resistant, (black) jacket system that does not require the direct bonding required for traditional (yellow) CSST products.
Can I bond CSST to water pipe?
CSST shall not be supported on or by other electrically conductive systems including copper water pipe, electric power cables, airconditioning and heating ducts, communication cables and structural steel beams.
Does Counter Strike need to be bonded?
Counterstrike® must be bonded in accordance with the National Electrical Code NFPA 70 Article 250.104 in the same manner as the minimum requirements for rigid metal piping.
Does flash shield need to be bonded?
a) There are no additional bonding requirements for FlashShield™ imposed by the manufacturer’s installation instructions. FlashShield™ is to be bonded in accordance with the National Electrical Code NFPA 70 Article 250.104, Canadian Electrical Code, CSA-C22.
Can you ground an electrical panel to a gas line?
In summary, you cannot use a metal underground gas piping system as a grounding electrode. However, you must bond the piping system to the grounding electrode system for safety reasons.
Is earth bonding still required?
Supplementary equipotential bonding (between waste pipes, metallic service pipes and earth connections of bathroom equipment) is no longer required if, and only if, the main bonding between metal service pipes can be proved to be continuous.
Where do you bond the gas line?
Corrugated stainless steel tubing (CSST) gas piping systems shall be bonded to the electrical service grounding electrode system at the point where the gas service enters the building. The bonding jumper shall be not smaller than 6 AWG copper wire or equivalent.
Is gas bonding a legal requirement?
As of 2008, earth bonding is a legal requirement for any electrical installations in rooms that contain a shower or bath. The term ‘earth bonding’ refers to the use of a thick green and yellow copper cable to connect your gas meter or consumer unit to incoming supplies such as your gas pipe.
What is bonding vs grounding?
Bonding. Bonding is the connection of non-current-carrying conductive elements like enclosures and structures. Grounding is the attachment of bonded systems to the earth. Both are necessary to safeguard people and property from electric hazards.
What size wire do you bond gas pipe with?
The bonding conductor must not be smaller than a 6 AWG copper wire or the equivalent size if made of aluminum. The means for attaching the bonding conductor to the grounding electrode system must be in accordance with NFPA 70. The bonding conductor must be not longer than 75 feet (22,860 MM).
How much does it cost to ground a CSST line?
How Much Does It Cost? As with most electrical repairs the cost can vary significantly based on many factors, but a good rule of thumb would be between $150 – $500 for most single-family homes in Central Iowa.